Material selection for superheaters and reheater plays a very critical role in ensuring performance and availability of boiler. Any long term overheating failure of tubes in superheater or reheaters near the transition points needs investigation by designers.
In large capacity boilers with high superheat temperature of the order of 540 degree C and above, it is practically not economical to use a single material. The main single reason for this is due to the fact that the steam from steam boiler drum enters the superheater around 350 deg C and leaves around 540 deg C. As the steam travels from the drum take-off pipes to the roof tubes to the low temperature tubes and high temperature superheater outlet, it picks up temperature at each unit length of tube.
Keyword: Industry steam boiler,Boiler Design, Materials in super heaters
This process changes the metal temperature of the tubes at each unit length of the tube. As the metal temperature of any tube increases there is a drop in the hoop strength of the tube material. This makes the requirement more stringent to the designers by forcing them to increase the thickness required to withstand the internal pressure in the tubes. However, because the thickness of the tubes cannot be increased beyond a certain range, this makes it necessary to upgrade the material of the tube to accept the increase in temperature. Designers use materials starting from carbon steel, to low alloy steel, to high alloy steel, and then to stainless steel to meet the requirements of the increase in metal temperature of the tubes as the steam picks up temperature in superheaters.
The location where such material transition requirement is fixed by the designers based on the margin between the allowable temperature for the material and the calculated metal temperature at the tube length. It is very critical to select this point correctly to avoid any tube failures in the superheaters. The point at which the difference between the allowable metal temperature and the predicted metal temperature can vary due to other reasons like low steam flow through the section of superheater due to high de-superheating water quantity, the upset in the radiation heat in the area, excess area for heat transfer provided, over loading of the unit, etc.
Correcting the transition point in any heat transfer surface like a superheater, reheater, etc. will be possible only with a long shutdown and a large volume of in-situ welding. The lower grade material will have to be upgraded suitably to have an adequate margin between the allowable temperature and the operating metal temperature. Any long term overheating failure near the transition point or at the transition point will need a very detailed review by the designers. The failed sample of the tube will have to be metallurgically evaluated for the reason of failure and the temperature to which the tube had been subjected.
Packaging Detail:Wooden box package of Boiler Designers Use Different Materials in Super heaters
Delivery Detail:20-40 days after payment
We have over 70 years' experience of industrial steam boiler and autoclave, and we have a professional installation and after-sales staff for products.Take advantage of the most economical way to improve efficiency and operating flexibility, Get substantial savings on your fuel costs,Reduce all emissions for each K/W of electricity generated, including CO2.
Our industrial steam boiler manufactured strictly according to national and international standard. our products have approved ASME, IBR, ISO9001-2008, etc
All our company's products are 100% factory inspected to ensure the high quality.
We provide one year quality warranty service, please rest assured purchase.
ZG service ensures that this will not happen. During installation of industrial steam boiler, 1-2 experienced engineering and technical personnel will be sent for the site representative for technical tests and installation instructions free of charge; processing the various problems arising in the course timely while installing.
Number of Employees:above 1500 People
Our products:industrial horizontal steam boiler and hot water boiler(biomass boiler, gas boiler, oil boiler, coal boiler, etc), CFB boiler, power plant boiler, waste heating recovery boiler, Pressure Vessel(AAC autoclave, Curing tank,etc )
Factory Size (Sq.meters):400,000 square meters
Factory Location:Factory 1: Zhengzhou,,Henan, China. Factory 2: Xingyang,Henan,China
Number of R&D Staff:376 people
Total Annual Sales Volume:US$100 Million
Main Market:South America(Colombia, Venezuela, Guyana, Suriname, Ecuador, Peru, Brazil, Bolivia, Chile, Paraguay, Uruguay, Argentina and French Guiana), North America(Bahamas, Canada, Costa Rica, Cuba, El Salvador, Guatemala, Honduras, Haiti, Jamaica, Mexico, Nicaragua, Panama), Eastern Asia(Mongolia / Russia / North Korea / South Korea / Japan), Oceania(Australia, New Zealand, Fiji), Mid East(Bahrain, Egypt, Iran, Iraq, Israel, Jordan, Kuwait, Lebanon, Oman, Qatar, Saudi Arabia, Syria, UAE and Yemen, Palestine, Algeria, Libya, Morocco, Tunisia and Sudan, Mauritania and Somalia), Africa(Egypt, Sudan, Libya, Tunisia, Algeria, Morocco, Ethiopia, Somalia, Kenya, Tanzania, Sierra Leone, Liberia, Cote d'Ivoire, Ghana, Togo, Niger, Nigeria, Cameroon, Gabon, Congo (Brazzaville), Zambia, Zimbabwe, Angola, Mozambique, Botswana, Namibia, South Africa), South Asia(Nepal, Bhutan, India, Pakistan, Bangladesh, Sri Lanka, Maldives) Southeast Asia(Vietnam, Laos, Cambodia, Thailand, Myanmar, Malaysia, Singapore, Indonesia, Brunei, the Philippines, East Timor) Domestic Market(China)
Get Price And Support
Simply complete the form below, click submit, you will get the price list and a ZG boiler representative will contact you within one business day. Please also feel free to contact us by email or phone. ( * Denotes a required field ).
Email: [email protected]
Tele: +86 17719993430